AC Maintenance Air Conditioning Repair, Air Conditioner Installation & Air Conditioner Repair in Land O'Lakes, FL
Bay Area Air Conditioning, Inc. has been serving home and business owners in Land O’Lakes and Citrus, Hernando, Pasco & Hillsborough Counties for 46 years. We go above and beyond to provide reliable, cost-effective results, and we never cut corners to save a buck. Our technicians are certified and factory trained to provide superior heating, cooling, and air quality solutions that are tailored to your specific needs. Our goal is to create safe, healthy, and comfortable indoor environments. Contact us today to schedule an appointment with one of our dedicated professionals.
Air Conditioner Repair & AC Repair in Land O'Lakes, FL
for Land O' Lakes, FL
Nancy - Land O' Lakes, FL
Very efficient, helpful and polite
Jeremy - Land O' Lakes, FL
Very knowledgeable and informative as to the next steps to take.
Stephen - Land O' Lakes, FL
Came out same day over the holidays. Gave us great information and important tips.
Service tech VERY knowledgable
Joy - Land O' Lakes, FL
The technician Came on time and got to work checking over my recently installed Carrier unit. There was a small odor intermittently from my air —“ conditioner “ that is an add on to my Carrier unit . It’s purpose is to prevent mold or allergens in my house. It makes peroxide naturally and I was not sure why it smelled like peroxide off and on. I was assured it’s no big deal to dial it back a bit and there will be no odor , I was told That the Add on to my Carrier unit will still remove allergens from of the air. Yea!! My daughter said my house smells really clean and fresh which was a bonus,,because a HEALTHY house was my goal. Joy The service call was a follow up, so no cost to me.
Lisa - Land O' Lakes, FL
Cliff was professional, thorough, knowledgeable and have great tips and answered all of my questions and concerns. Will definitely be using Bay Area A/C again!
Nancy - Land O' Lakes, FL
The technician was very knowledgeable, efficient, professional and polite. Very satisfied
Great service and price
Dawn - Land O' Lakes, FL
Dawn - Land O' Lakes, FL
Clint - Land O' Lakes, FL
Best Service Ever
Bob - Land O' Lakes, FL
We usually get good service from your service technicians. However, Jeff went above and beyond and performed additional checks. A most thorough job, Jeff! Thank you.
Pete is excellent!
Jan - Land O' Lakes, FL
Pete is knowledgable, explains issues in layman terms and doesn’t try and sell you something you don’t need. Very trustworthy!
High charged price, lousy service
Edwin - Land O' Lakes, FL
Tech was very pleasant but odie was not taken care of problem still persist. Not sure if will ever use them again
Thoroughly positive experience
The Robbins - Land O' Lakes, FL
rep went over everything before signing contract for new system.
hudson - Land O' Lakes, FL
this Email was lost in overwhelming email ads. Sorry. We have reccommended your services to our neighbor across the street in the Groves.
Hudson - Land O' Lakes, FL
Sorry so late in gettng back to you. Message was lost in email ads overload.. Reccommended your services to neighbor across the street in the Groves. She needs a nee system
Jeri - Land O' Lakes, FL
Totally satisfied with our system and the customer service Bay Area provides
Gosnell - Land O' Lakes, FL
Pete was vey thorough and helpful. He was most courteous and very pleasant.
Recent AC System Check and TuneUp
Porzio - Land O' Lakes, FL
Bay Area has treated us so well since we moved here in 2003 and Robert's visit today was no different. He was on time, knowledgeable and kept me totally informed of his progress. Thanks so much for keeping our AC running at it's best. Well done...
Miller - Land O' Lakes, FL
Dave was fast, professional, answered our questions, very knowledgeable and very polite.
Steele - Land O' Lakes, FL
Your service rep was very knowledgeable and answered all our questions.
groomes - Land O' Lakes, FL
Claire - Land O' Lakes, FL
Pete is thorough and courteous
Peters - Land O' Lakes, FL
System maintenance on heatpump system. Replaced FILCAB filter and two UV bulbs
Commercial cleaning and tune up
Commercial system cleaning and tune up.
Need to return to complete cleaning and install float safety switch
System was low on 410a refrigerant. Added 5 pounds to get unit working and advised custmer to be ready for system replacement soon. Suspect refrigerant leak in under ground lineset. Recommend replacement of lineset too when system gets replaced.
Cleaned out drain line that was severely blocked with heavy scale build up. Purged and flushed drain line. Restarted and tested cooling and drainage. Charged holiday rates.
2nd floor system. Cleaned indoor coil with coil cleaner and rinsed throughly. Vacuumed and cleaned drain line. Added drain tablets and viper pan spray. Sprayed entire coil and inside cabinet with disinfect. Restarted cooling and tested . Customer is not able to detect smell anymore.
Unit operating on arrival. Gather system information. Advise customer of service contract and warranty information.
System off on float safety switch. Flushed drain and pan, not much in drain line. Inspected drain pitch from unit to where it turns down wall. Good pitch. Tested drain for 20 minutes, all operating properly.
Upon arrival I found a crack in an pvc 90 degree elbow. I cut it out and reinstalled a new elbow. I reinstalled rubbatex and tested with a lot of water down drain. It is not leaking at this time.
Sealed around all leaks on supply plenum with spray glue ,tape and mastic. Added more duct washers to return plenum. Already had washers under mastic. Adjusted Remi halo per customer. Warranty.
Recall. Had to clear condensate pump discharge line under house again. Cycled pump several times to make sure it would drain. Discharge line may need to be rerouted if problem becomes worse in future. Discharge line is only 3/8" copper.
Cleaned out blocked drain line trap under unit in laundry room. Also cleaned out condensate pump and primary drain pan. Added drain tablets and viper pan spray. Restarted cooling and tested drain line and condensate pump several times.
3.5 ton heatpump
Found compressor shorted to ground and not repairable anymore. System is 15 years old and is using old R22 that is being phased out of production. Do not recommend replacement of compressor due to age and R22 phase out. Quoted for new system Extended labor warranty $720.
Found indoor X13 blower motor starting and stopping intermittently. Factory motor will need to be ordered and replaced Cost is pending 312 218 3560 to quote price
Checked air handler, unit is clean. No evidence of any growth. Coil is new recently replaced. Checked ductworworfor rips, tears or leaks
System off on float safety switch. Flushed drain and pan. Treated with drain solve
Found failed outdoor, replaced motor. Test and check system
Tested cooling . Checked puron levels and temperature drop on indoor coil. Adjusted humidity control. System did not make any unusual noise at this time and has proper temperature drop on indoor coil. Recommend using standard air filters for best airflow Warranty.
16 SEER 10 year parts and 1 year labor warranty
service call completed, safety switch open on arrival, drain and flush condensation line , drain line heavily clogg, advised client to replace air filters regularly, all systems vital are good at this time
Found the system low on 410a. Added 2.3 pounds of 410a and searched for the leak. Wasnt able to locate the leak. I wasn't able to get to the back side of the evaporator coil. The leak could be there.
Looked at job to added supply vent to kitchen and seal up old vent. Cost will be $150
system up and running when arrived. Customer stated was down for 2 hours. Checked drain, checked blower (possible x13 intermittent problem), cjecked capacitors. Found 45/5 cap measuring 36.8/4.6. Replaced capacitor.
Replaced dual cap. System operating at this time. Recommend PM yearly.
Found system running at a very low suction pressure. System is running with fixed metering device and has no tx valve. Inspected system for refrigerant leak and found none. Added one pound of 410a to get system working and achieved a 19 degree temperature drop across indoor coil. Need to recheck system again early next week to see if any refrigerant is lost. Suspect possible restriction in metering device. ICP COMFPRT MAKER INDOOR FEM4P3000AL3. A162974306 OUTDOOR CSH530GKA200 E162626890
System was off on float switch safety. Cleared obstruction and cleaned and flushed drain line. Added disinfectant to drain line and pan. Restarted and tested drain line.
Found outdoor unit void of all refrigerant charge. Added small amount of 410a to locate leak. Found 2 leaks. Top of accumulator has small leak but more immediate is high voltage wire worn through insulation and shorted hole in copper tubing. Reccomend replacement due to age and condition.
A/C Service & Installation You Can Trust
Land O’ Lakes, FL
At Bay Area Air Conditioning, Inc., we aim to earn your trust through quality customer service and results that speak for themselves. When it’s time for a seasonal inspection, call us for a Higher Performance Tune Up and Cleaning. Our thorough Tune Up ensures maximum value of your investment by enhancing system longevity and efficiency. If you’re ever in need of a repair, we’ll send a specialist to your home or business at a time that works for you. We repair all makes and models, and can resolve most challenges in a single visit.
As a Carrier Factory Authorized Dealer, we carry a large inventory of industry-leading systems. We’ll work with you to identify the right products for your comfort needs. We stand behind our work by offering a ten year parts and labor warranty. Contact Bay Area Air Conditioning, Inc. for air conditioning service, repair and installation in Land O’Lakes, FL.