Air Conditioning Repair, Air Conditioning Installation & AC Service in Hudson, FL
Bay Area Air Conditioning, Inc. is your trustworthy source for a complete range of HVAC services in Hudson, FL. Know that we don’t earn your business by cutting quality. As a Carrier Factory Authorized Dealer, we draw from industry leading and proven reliable heating, cooling, and air quality options. Taking advantage of unprecedented energy efficiency, outstanding warranties, and smart technology, we trim the cost of operation and ownership, while enhancing comfort and control over your indoor environment. At Bay Area Air Conditioning, Inc., we focus on long-term value, and improve the enjoyment of your home or office through exacting standards of job performance. Contact us at (888) 324-4033 for new installation, equipment upgrades, seasonal maintenance, repair, and duct sealing.
Air Conditioning Installation & AC Installation in Hudson, FL
for Hudson, FL
Christine - Hudson, FL
Great tech, very knowledgable.
Great Service and Excellent Tech!
Kenneth - Hudson, FL
Matt Clanton did awesome job diagnosing the problem,finding out if the part was still under warranty to help save me money,and installing my new blower motor.Very happy with the quick service! 😁
Great service! Super timely!!
Ronda - Hudson, FL
Dave - Hudson, FL
Tech was a little late in the evening for a Tune-Up service but made up with his thoroughness. Great job !
Dan - Hudson, FL
Arrived on time. Performed tests and advised quickly
Susan - Hudson, FL
Technician was professional and pleasant. My AC is about 17 yrs old. It was working fine when I called Bay Area. However I hadn't lived in the house wanted to make sure I wasn't going to have any issues. I expected a sales pitch at the end of the appointment. You know the one...Old unit time, for a new one etc. When I asked the technician if I should be concerned with anything I was told that he didn't see any issues with the unit! AWESOME AND HONEST! Will definitely use Bay Area AC again. I only gave a 4 star in price because I had a competitors coupon for 1/2 the price. I had originally scheduled them come out. My husband didn't know and made appointment with Bay.
Phil - Hudson, FL
He came over right away, was very through, unfortunately he wasn't able to solve our problem but he did find out it was our router connection and pointed us in the right direction
Jenny - Hudson, FL
Excellent experience - happy with service. Technician should have worn a mask. He did not.
Jane - Hudson, FL
Great customer service, fair pricing and quick resolution of AC problem. Thankyou and will be calling you to n the future.
Beverly - Hudson, FL
Morrell - Hudson, FL
My experience with this company is very satisfying!! The response time is beyond expectations!! They did not quit unti they were able to troubleshoot my heating issues and fixed it.
Very Responsive Company!!
Morrell - Hudson, FL
Excellent and Professional service.
Larry - Hudson, FL
Matt was the technician that worked on the air and heat and did a very good job. He found the problem and we are good to go. Thankyou. Larry. Dobiak
Maria - Hudson, FL
Jeff knew just what the issue was,and fixed it in a fast and friendly way.
Colin - Hudson, FL
Steve - Hudson, FL
I would recommend this company
John - Hudson, FL
Great Tech & Tuneup
Brian - Hudson, FL
I have had a great experience with this company from when I replaced my system 7 years ago and again today when I had the drain line cleaned out and an annual tuneup. The Tech was very professional and informative and the cost of the service was very reasonable.
Dan - Hudson, FL
Top notch service
great service .the best of the best
Michael - Hudson, FL
my 3rd experience.honestly could not ask for better service.the problem was solved in the first 10 minutes .2x at my place and once at my moms.i already recommended them to 2 of my neighbors.
Beverly - Hudson, FL
Great Guy Mark
Great service , Thorough and Honest !
Mark - Hudson, FL
Peter Was on time , thorough and honest ! Glad I choose Bay Area Air Conditioner . Had other companies in the past tell me I needed thing's that I knew I didn't need , just to jack up the price . very satisfied!
Kathy - Hudson, FL
Cliff was very professional and did a great job providing service to our ac unit
Beth - Hudson, FL
Everyone was so nice, professional, helpful and prompt!
Shirley - Hudson, FL
Pete knows what he is doing. Nice to see a familiar face to do my service.
Very professional and competent.
Lisa - Hudson, FL
Ive used Bay Area for well over 15 years and have never been disappointed
Pat - Hudson, FL
Honest, Reliable Service
Jan - Hudson, FL
Peter has the technical expertise to fix your HVAC issues. Did not try and sell us something we don’t need.
Great service. I called and he came out within hours and fixed my problem.
Sears - Hudson, FL
James - Hudson, FL
Was quick and knowledgeable
10 years parts 1 year labor
Found the system freezing up due to a bad blower capacitor. Replaced the capacitor and checked the freon level. 63.1 psi over 220.1
SYSTEM MAINTENANCE ON HEATPUMP SYSTEM.
Upon arrival I took pictures of what it looked like. Then I removed the 2 duct covers. I reversed them putting the more ridged piece on bottom for support to take dip out of middle. Then I reattached and sealed with tape and caulk. Then I labeled unit per Doug. Then I added a clamp 12 inches from disconnect. Paper work was put in place yesterday per Greg. It should pass inspection at this time. I took pictures of final repairs.
Closed out for year end. If customer calls please re do invoice.
service call completed, check electrical components, dual capacitor open on arrival, replaced defective component, tested equipment operations, all systems vital are good at this time, recommended scheduling a system tune up
System maintenance on heatpump system. Found slow leak in evaporator coil. System is almost 14 years old. Recommend new system when possible Frigidaire Model B5BM T25K A
Maintenance completed, drain and flush condensation line, advised client to replace air filter regularly, clean evap coil and conderser coil, check system operations, advised client system condition, unit is 12 years old, coil are showing moderate signs of rust, due the system age it may cause brake down or refrigerant leaks , at this moment the system is operating within manufacturing specifications, send system replacement quote on the email on file, financing options are available
Found system low on refrigerant due to leak in evaporator coil. Coil will need to be replaced . COST for new trane coil $3715 System is 10 years old. May want to consider system replacement. Left quote for new equipment. Recall.
Install emp. blower motor ....
Drain line was clogged and pleated filter so dirty was sucked out of cardboard frame, also no trap in the drain line (air could be heard grugging at outlet) Installed 90Â° ell for trap and vacumed drain line 12 Ã— 24 filter needed asap Noted Outdoor unit condenser coil full of heavy oxidation (causes poor bth/hr transfer) Indoor unit evaporator very dirty entering air side System dates to 2008,, Quoting new system
Upon arrival I knocked on front door upstairs,side door down stairs and back French doors. No one answered. I call owner. She tried calling tenant. No answer she had me take pictures of doors to be able to show tenant I was there.
Found a bad capacitor within the condneser. Replaced the capacitor. And tested the systems operation. I gave the customer the option to get the factory capacitor for only a labor charge but she decided to go with the American Made Capacitor that we stock on our trucks.
Upon arrival the Coleman gas was not ignite. Gas valve and power off to unit. I turned system on and tried to light pilot. I checked voltage to valve and had the required 24 volts. The gas valve was not allowing gas to flow through. Gas valve needs replaced. I dicussed at length on eliminating system and in stalling a heat pump. She is going to get estimates from gas company to replace gas valve.
Found small area of algae in primary pan causing water level to be higher than normal and subsequent drain safety activated. Cleared algae abap and treated pan with Viper enzyme. Recommended tenant use a lesser type pleated filters
3/8/2021: Customer needed to reschedule. 3/19 Annual ac tuneup and cleaning. I checked refrigerant pressures and static pressure. I checked temp splits. I checked amp draws and heat strip. I checked capacitor and contactor. I waxed outdoor unit and cleaned both coils. I flushed drainline multiple. I got equipment info. I did not find any problems at this.
Service call completed, compressor wasn't energized dua a open dual cap , replaced defective component, check system operations, strongly recommended to scheduled a system tune up, system is operating at this time
Air filter delivered and installed
Drain severely clogged. Clear drain and pan. Treat with drain treatment. System operating and draining at this time. 55* at supply plenum.
Upon arrival nothing was running. I went into attic and found float switch pointing down. I leveled float switch and system started. I checked drain and seemed to be clear but i flushed anyway. It is cooling at this time. Credit card all in to office.
Ran complete system tune up. Found no problems with the system other than needing a new filter. System working within factory specifications.
Maintenance completed, drain and flush condensation line, advised client to replace air filter regularly, clean evap coil and conderser, check electrical components and refrigerant pressure, all systems vital are good at this time
I called customer and they want to buy new package unit. I notified office to contact homeowner with financing and install date.
AH breaker tripped, reset, check system operation. 50 amp breaker with 10Kw heat strip. Advise customer of breaker sizes, declined breaker replacement. System operating at this time.
Found a tripped float switch. Treated, flushed, and tested the drain line. The system is starting to rust on the bottom and I suspect the air handler is filling up with water. Due to the age and seer of the system I would recommend the system to be replaced.
System cleaning and tune up
Found blower motor failed. Need new motor
maintenance completed, check system operations, advised client to replace air filter regularly, upon arrival, drain system heavily clogg, drain and flush condensation, clean condenser coil and evap coil, check electrical components and refrigerant pressure, system is operating within manufacturing specifications
Blower motor failed Replaced motor and tested
Blank stat. Replaced spade fuse and check operation. System operating at this time. Recommend purchasing a Service contract as system is out of warranty.
Expert A/C Service & Installation Throughout Hudson, FL
Bay Area Air Conditioning, Inc. adheres to strict installation and service procedures to ensure superior return from your investment. A seasonal Higher Performance Tune Up and Cleaning keeps your essential HVAC equipment operating more reliably and at peak condition. For any difficulties with any makes or models of heating, cooling, or air quality equipment, we offer free second options, prompt scheduling, and long-term repair solutions. All new installation projects are protected by our ten year parts and labor warranty, and after completion, we familiarize you with operation and features, and verify performance data. Call on Bay Area Air Conditioning, Inc. for expert HVAC services in Hudson and Citrus, Hernando, Pasco & Hillsborough Counties.