Air Conditioning Installation, Air Conditioner Repair & Air Conditioning Repair in Hudson, FL
Bay Area Air Conditioning, Inc. is your trustworthy source for a complete range of HVAC services in Hudson, FL. Know that we don’t earn your business by cutting quality. As a Carrier Factory Authorized Dealer, we draw from industry leading and proven reliable heating, cooling, and air quality options. Taking advantage of unprecedented energy efficiency, outstanding warranties, and smart technology, we trim the cost of operation and ownership, while enhancing comfort and control over your indoor environment. At Bay Area Air Conditioning, Inc., we focus on long-term value, and improve the enjoyment of your home or office through exacting standards of job performance. Contact us at (888) 324-4033 for new installation, equipment upgrades, seasonal maintenance, repair, and duct sealing.
Air Conditioning Installation & Air Conditioner Repair, in Hudson, FL
for Hudson, FL
Susan - Hudson, FL
Technician was professional and pleasant. My AC is about 17 yrs old. It was working fine when I called Bay Area. However I hadn't lived in the house wanted to make sure I wasn't going to have any issues. I expected a sales pitch at the end of the appointment. You know the one...Old unit time, for a new one etc. When I asked the technician if I should be concerned with anything I was told that he didn't see any issues with the unit! AWESOME AND HONEST! Will definitely use Bay Area AC again. I only gave a 4 star in price because I had a competitors coupon for 1/2 the price. I had originally scheduled them come out. My husband didn't know and made appointment with Bay.
Phil - Hudson, FL
He came over right away, was very through, unfortunately he wasn't able to solve our problem but he did find out it was our router connection and pointed us in the right direction
Jenny - Hudson, FL
Excellent experience - happy with service. Technician should have worn a mask. He did not.
Jane - Hudson, FL
Great customer service, fair pricing and quick resolution of AC problem. Thankyou and will be calling you to n the future.
Beverly - Hudson, FL
Morrell - Hudson, FL
My experience with this company is very satisfying!! The response time is beyond expectations!! They did not quit unti they were able to troubleshoot my heating issues and fixed it.
Very Responsive Company!!
Morrell - Hudson, FL
Excellent and Professional service.
Larry - Hudson, FL
Matt was the technician that worked on the air and heat and did a very good job. He found the problem and we are good to go. Thankyou. Larry. Dobiak
Maria - Hudson, FL
Jeff knew just what the issue was,and fixed it in a fast and friendly way.
Colin - Hudson, FL
Steve - Hudson, FL
I would recommend this company
John - Hudson, FL
Great Tech & Tuneup
Brian - Hudson, FL
I have had a great experience with this company from when I replaced my system 7 years ago and again today when I had the drain line cleaned out and an annual tuneup. The Tech was very professional and informative and the cost of the service was very reasonable.
Dan - Hudson, FL
Top notch service
great service .the best of the best
Michael - Hudson, FL
my 3rd experience.honestly could not ask for better service.the problem was solved in the first 10 minutes .2x at my place and once at my moms.i already recommended them to 2 of my neighbors.
Beverly - Hudson, FL
Great Guy Mark
Great service , Thorough and Honest !
Mark - Hudson, FL
Peter Was on time , thorough and honest ! Glad I choose Bay Area Air Conditioner . Had other companies in the past tell me I needed thing's that I knew I didn't need , just to jack up the price . very satisfied!
Kathy - Hudson, FL
Cliff was very professional and did a great job providing service to our ac unit
Beth - Hudson, FL
Everyone was so nice, professional, helpful and prompt!
Shirley - Hudson, FL
Pete knows what he is doing. Nice to see a familiar face to do my service.
Very professional and competent.
Lisa - Hudson, FL
Ive used Bay Area for well over 15 years and have never been disappointed
Pat - Hudson, FL
Honest, Reliable Service
Jan - Hudson, FL
Peter has the technical expertise to fix your HVAC issues. Did not try and sell us something we don’t need.
Great service. I called and he came out within hours and fixed my problem.
Sears - Hudson, FL
James - Hudson, FL
Was quick and knowledgeable
5 Stars service
Deb - Hudson, FL
Called and the next day had more questions. 5 stars with receptionist all the way to manager QUICK response..ALL my questions answered and resolved. This is why they have excellent reviews. I will refer them
Willard - Hudson, FL
Pete was on-time, friendly, knowledgeable.
Prompt and efficient service
Fowler - Hudson, FL
Great Staff -timely and efficient
Sullivan - Hudson, FL
Ann - Hudson, FL
Professional as always.
annual ac tuneup and cleaning. I refrigerant pressures and staic pressures. I checked all amp draws. I checked temp splits. I waxed outdoor unit. I cleaned both coils. I flushed drainline with dawn. I did not find any issues at this time. i got equipment information
Found t- stat shorting out in heat mode. Replaced stat and looked through history and can't find any references to us installing stat with system. Talked with Dale and we need to reschedule and install a Emerson Easy View stat. That way it will be warranty. Stat i installed is temporary until new stat comes in.
Per customer, heat working up until they changed their router (alexa) Verified control wires are capable of completing signals Customer will attempt to connect new router to stat
system maintenance on heatpump system.
system checkout & cleaning Noted both outdoor & indoor coils were dirty, cleaned both System is operating within normal parameters for its age
Completed the maintenance inspection.
upon arrival everything would start except compressor. I found capacitor swollen and open. After quoting price I replaced. I checked pressures and the system is cooling.
System was running upon arrival. Found heavy slime build up in drain line . Suspected float switch was opening a d then closing intermittently due to slow drain. Cleaned and flushed drain line. Restarted and tested drain line and cooling
evaporator was found 100% matted, cleaned abap, have 60% to 70% cleaner,customer is recommended to have another evaporator cleaning just after summer start
Breaker was tripped 1/2 way was putting out 110v flipped breaker back on unit is running properly. Customer wants new breaker installed.
Reschedule for tomorrow. Customer having problems with stat.
service call completed, compressor wasn't not operating upon arrival, check electrical components , capacitor not operating, replace defective component and test compressor operations, during diagnostic found the thermostat not sending the signal to the heat element energized, isolated wires and manually energized heat components and is fully operational, advised client that the thermostat need replacement if the need of the electrical heat source, at this moment system is heating and cooling, advised to replace air filter regularly
On arrival dnstrs star was set at 78 and reading 77, system was running, thru discussion w it customer she had raised temp from 74 to 78 approximately 1hr prior. Upstrs stat was set at 80Â° and reading 80Â°.Temp test at 60Â° outdood Return air 84Â° and supply was 105Â° with second stage supply was 140Â° System function normal Comparing dnstrs to upstrs most all heat produced from dnstrs will rise to second floor
Service call completed, client stated thermostat was reseting itself, check system operations upon arrival, removed batteries that client installed, replace air filter, check system operations , no problem found at this moment, all systems vital are good at this time
Recall. Removed jumper in outdoor unit that was causing system to run in cooling regardless of thermostat setting . Tech 930 corrected thermostat configuration yesterday. Jumper was possibly left on by tech from previous company.
Tune up complete Replaced infinity air filter
When arrived checked system in heat. Found air handler blower and electric heat running but heat pump not running. Found no call for outdoor unit from thermostat. Verified configuration and found tstsat configured for straight cool operation with electric heat only. Reconfigured thermostat for correct equipment type. All operating properly now.
found transformer blown on 24 volt side. Also found coil on contactor shorted to ground. Contactor 24 volt coil short caused transformer to blow ( burn out ). Installed new parts and tested system. Note: weak 24 volt coil on heat strip shorted and caused the issues.
Found a blown fuse within the air handler. Removed the fuse and searched for a short. I did find a damaged wire within the condenser and loose wiring at the thermostat. Repaired the wire and tightened the connections at the thermostat. 30 day warranty.
Annual ac tuneup and cleaning. I checked system operations. I checked amp draws. I checked static pressure and temp split. I waxed outdoor unit. I cleaned evaporator and condenser coil and purifier. I flushed drainline. I changed filter furnished by homeowner. No issues at this time.
Confirmed that blower motor has failed . Sent information to parts department. Cost of new motor is pending. Also left quotes for new system per customer request. System is about 10 years old. If customer decides on new system need to make sure existing electrical panel is up to code.
Defrosted system. Tested and found system low oh refrigerant. Leak searched system several times. Found freon steadily leaking at service port on evaporator coil. Tightened Schrader core and replaced plastic cap with brass cap to stop service port from leaking. Found no other leaks. Replaced lost refrigerant. Added three pounds of 410a
service call completed, 3 amp fuse blown upon arrival, check system and trace low voltage, found high pressure switch wire exposed and were making contact with Cooper tube from the compressor, isolated wires and replace fuse ( client provided fuse ) advised client system condition and provide with options for new system replacement send on the email on file , financing options are available call to scheduled
upon arrival the float was tripped. I removed panels and vacuumed slime from pan and drainline. Then I flushed drainline multiple times with dawn. The stat came back on and ready when set point is needed.
service call, system down upon arrival due client replace contactor, system has a reset push button, that can cause due a short or overload on the system, unit over 15 years old, system heavily impacted with rust, advised clients system condition, at this moment system is operating at this time
Blower module inoperable. Ordered new module. Parts warranty. Down.
Clear drain and pan. System operating at this time.
service call completed, glass fuse blown upon arrival, replace defective component, advised client to replace condesation pump , system is operating at this time.
Found unit off on float safety switch, drain clogged. Cleared drain and pan. All operating properly.
system down and out , blower motor need replacement, call client to schedule part replacement, adjust thermostat wall plate with the job
Expert A/C Service & Installation Throughout Hudson, FL
Bay Area Air Conditioning, Inc. adheres to strict installation and service procedures to ensure superior return from your investment. A seasonal Higher Performance Tune Up and Cleaning keeps your essential HVAC equipment operating more reliably and at peak condition. For any difficulties with any makes or models of heating, cooling, or air quality equipment, we offer free second options, prompt scheduling, and long-term repair solutions. All new installation projects are protected by our ten year parts and labor warranty, and after completion, we familiarize you with operation and features, and verify performance data. Call on Bay Area Air Conditioning, Inc. for expert HVAC services in Hudson and Citrus, Hernando, Pasco & Hillsborough Counties.