Air Conditioning Installation, Air Conditioner Repair & Air Conditioning Repair in Hudson, FL
Bay Area Air Conditioning, Inc. is your trustworthy source for a complete range of HVAC services in Hudson, FL. Know that we don’t earn your business by cutting quality. As a Carrier Factory Authorized Dealer, we draw from industry leading and proven reliable heating, cooling, and air quality options. Taking advantage of unprecedented energy efficiency, outstanding warranties, and smart technology, we trim the cost of operation and ownership, while enhancing comfort and control over your indoor environment. At Bay Area Air Conditioning, Inc., we focus on long-term value, and improve the enjoyment of your home or office through exacting standards of job performance. Contact us at (888) 324-4033 for new installation, equipment upgrades, seasonal maintenance, repair, and duct sealing.
Air Conditioning Repair & Air Conditioner Repair, in Hudson, FL
for Hudson, FL
Colin - Hudson, FL
Steve - Hudson, FL
I would recommend this company
John - Hudson, FL
Great Tech & Tuneup
Brian - Hudson, FL
I have had a great experience with this company from when I replaced my system 7 years ago and again today when I had the drain line cleaned out and an annual tuneup. The Tech was very professional and informative and the cost of the service was very reasonable.
Dan - Hudson, FL
Top notch service
great service .the best of the best
Michael - Hudson, FL
my 3rd experience.honestly could not ask for better service.the problem was solved in the first 10 minutes .2x at my place and once at my moms.i already recommended them to 2 of my neighbors.
Beverly - Hudson, FL
Great Guy Mark
Great service , Thorough and Honest !
Mark - Hudson, FL
Peter Was on time , thorough and honest ! Glad I choose Bay Area Air Conditioner . Had other companies in the past tell me I needed thing's that I knew I didn't need , just to jack up the price . very satisfied!
Kathy - Hudson, FL
Cliff was very professional and did a great job providing service to our ac unit
Beth - Hudson, FL
Everyone was so nice, professional, helpful and prompt!
Shirley - Hudson, FL
Pete knows what he is doing. Nice to see a familiar face to do my service.
Very professional and competent.
Lisa - Hudson, FL
Ive used Bay Area for well over 15 years and have never been disappointed
Pat - Hudson, FL
Honest, Reliable Service
Jan - Hudson, FL
Peter has the technical expertise to fix your HVAC issues. Did not try and sell us something we don’t need.
Great service. I called and he came out within hours and fixed my problem.
Sears - Hudson, FL
James - Hudson, FL
Was quick and knowledgeable
5 Stars service
Deb - Hudson, FL
Called and the next day had more questions. 5 stars with receptionist all the way to manager QUICK response..ALL my questions answered and resolved. This is why they have excellent reviews. I will refer them
Willard - Hudson, FL
Pete was on-time, friendly, knowledgeable.
Prompt and efficient service
Fowler - Hudson, FL
Great Staff -timely and efficient
Sullivan - Hudson, FL
Ann - Hudson, FL
Professional as always.
timely service good technician
Fuge - Hudson, FL
great service fast and courteous
Dorothy - Hudson, FL
Joan - Hudson, FL
Always happy with the service
Fran - Hudson, FL
Quick and reliable service
George - Hudson, FL
Very happy with Bay Area A/C and they always exceed my expectations
high price for not working
David - Hudson, FL
spent 600 dollars yesterday and air is not working keeps freezing up. We are having a new unit put in with you soon but not happy today.
OUTSTANDING. Customer Service
Maureen - Hudson, FL
Thank you very much Bay Heating &Air. Unfortunately our home had been struck by Lightening last Monday night. Your service team came right to our rescue as our recently purchased air conditioner was effected by this weather event. Your service man worked diligently throughout the day after the lighting storm to restore and repair our air conditioner. As you well know it can get very hot here in Florida, and last Tuesday was no exception. The repairman was polite, and informed us as to what steps he was taking to get our equipment repaired perfectly. And since our air. Conditioner was under warranty we did not have to pay any money for this Outstanding service. thank you again for your continued great customer service. It really means a lot to us as senior citizens with major health problems. Sincerely, The Godleski’s
as always, prompt aervicw
Gilbert - Hudson, FL
Impressed that Pete arrived within a few hours of my call.
Blenda - Hudson, FL
Have always been happy with Bay Area service. That’s why I called today. Happy again.
Maintenance completed, drain and flush condensation line, advised client to replace air filter regularly, check electrical components and refrigerant pressure, clean condenser coil and evap coil, all systems vital are good at this time
upon arrival the homeowner said it quit working so she shut it off. I turned system on and it started. I checked capacitor on blower and condenser unit. Both are getting weak but not enough to replace at this time. I checked pressures and head pressure was a little high at 390. I noticed coil dirty so I used hose at unit to rinse coil. I also flushed drain line i noticed water setting in float that must of drained slowly to restart. It is cooling and draining at this time.
Upon arrival the blower module will not shutdown blower. I ordered new motor. He also bought a silver contract.
Upon arrival the homeowner said his super heat was too low. Last tech added refrigerant. When I first checked it in was around 10 degrees. Then after system running for 20 minutes it did drop to .5 degrees. I removed 1 lb of refrigerant that was added from last service call. superheated per homeowner is now 17. Homeowner wants refunded the 1 lb charged to him from last tech.
Blower motor not operating. Ordered new module. Warranty
Replace blower motor with control module
Check system operation. Add 1 lb. R22. System operating and draining at this time. Advise customer of refrigerant leak and recommend pressures checked in the spring.
system maintenance on 3 ton heatpump.
Service call completed, single pole contactor broken in the low voltage transform, replace defective components, all systems vital are good at this time
Clogged drain. Clear drain and pan. Check system operation. Cooling and draining at this time. Recommend yearly maintenance for system.
Replaced ID fan module. System operating at this time.
Upon arrival the capacitor was swollen and open. Would not stat compresser or fan. I replaced capacitor CAP455A
Completed the maintenance inspection. Found a clogged drain line and a weak capacitor. Flushed and treated the drain system. Replaced the weak capacitor. 40/1.2 reading. Rated for 45/5 MFD.
2- double head mini split systems. Cleaned indoor and outdoor coils and check operation. Both system operating and draining at this time.
Perform yearly maintenance checks. Added 1 lb R22. System operating and draining at this time. Inspect DW for new Upstairs unit and RS for repair.
SC to HP
drain clogged, flushed drain. Treated with detergent.
Service call completed, installed a thermostat provided by the client, check system operations, advised client that there is not warranty for the thermostat, all system vital are good at this time
water in pan at air handler, vacuumed out pan and flushed drIn. Checked charge, subcool high and superheated low. Adjusted charge to 7f subcool, superheated came up to 7 with 20.5f td.
Checked all grounds and power connections, bypassed airflow sensor. Replaced internal kit and airflow sensor. All operating properly
Found a bad capacitor. Replaced the capacitor and checked over the system.
Upon arrival I noticed secondary pan under airhandler rusted out and leaking into bucket. The drainline had backed up another company came out to clear drainline. I opened cabinet and found down spout off of coil causing water to drip over pan. I instructed tenant to run fan to help dry out. I could not get a hold of landlord for payment.
Quote to replace indoor circuit board
I installed metal protective covering over 3 ft of return duct per inspector. Ready for reinspection.
Found that the air handler is vertical in the garage. The supply plenum is sweating pretty bad. Adjusted the blower fan speed from low to high which increased the static pressure by .14 Old static reading: .33 New static reading: .47
Clear drain and pan. Check system operation. Add 1lb R410A. System operating and draining at this time.
Upon arrival I sealed the supply plenum that came loose and mastic. I added the 5th hurricane bracket to left back corner of condenser. I placed condenser manual in envelope on side of airhandler. I installed a post in front of airhandler. I removed the old drainline that inspector thought was for new unit. Ai5was moved from attic and there was two drainline. I put cap on old drainline at the chase. I order metal for return duct to be installed when it comes in.
Replaced factory indoor blower motor. Restarted and tested cooling and new motor. 58MV660006
Found air handler in attic sweating profusely. Took static pressure readings. In medium speed return static was .35 and supply was .30 inches wc. In high speed return static was .45 and supply was .40 Both tests were done with filter removed. Recommended to customer to not use pleated filters. Left system on high speed at this time and disabled humidity notifications as this system is not capable of independent dehumidification. Need to discuss with management about existing ductwork at this house.
Expert A/C Service & Installation Throughout Hudson, FL
Bay Area Air Conditioning, Inc. adheres to strict installation and service procedures to ensure superior return from your investment. A seasonal Higher Performance Tune Up and Cleaning keeps your essential HVAC equipment operating more reliably and at peak condition. For any difficulties with any makes or models of heating, cooling, or air quality equipment, we offer free second options, prompt scheduling, and long-term repair solutions. All new installation projects are protected by our ten year parts and labor warranty, and after completion, we familiarize you with operation and features, and verify performance data. Call on Bay Area Air Conditioning, Inc. for expert HVAC services in Hudson and Citrus, Hernando, Pasco & Hillsborough Counties.