for Clearwater, FL
Dennis - Clearwater, FL
As usual, Bay Area does a great job! Highly recommend them. The service man was courteous and did a wonderful job.
Excellent service, pleasant service man.
Deloris - Clearwater, FL
Got here right at 8 AM, did his work and on his way.
So far we are very happy with your service and pricing. Since 5 stars are perfect we may hold back a star just to keep you improving.
Gerald - Clearwater, FL
We had Dave check Freon which was up to specs. Dave also leak tested the A- coils and compressor and was not able to find any leaks. When the unit was installed the refrigerant lines were not replace since they run under the concrete floor through a conduit. We assume the lines are original and my be corroded and almost impossible to remove to install new lines but no one has attempted the task. We plan to have your company move the compressor off our patio and new lines installed at that time. However, we must gain approval and permits from On Top of the World Management. If they approve the move and issue a permit, we will contact you to complete the job.
Very professional, knowledgeable and friendly...all important to me!!!
Christine - Clearwater, FL
Every step of the way was efficient and professional. Very pleased and would refer to anyone with confidence.
Very efficient from the first phone call....very pleased
Nightwine - Clearwater, FL
Great Service, Great Employees
Marsha - Clearwater, FL
Have been a customer since 2012 and heartily recommend Bay Area! Thanks, Glenn!
Excellent response time on Saturday!
Marsha - Clearwater, FL
Great Service - As always!
PHIL - Clearwater, FL
morgan - Clearwater, FL
NEVER EXPERIENCED SUCH A GREAT CHECK UP...I WILL HIGHLY RECOMMEND GLEN HOLSAPPLE.
Shawn - Clearwater, FL
I live out of the area and have a rental condo in Clearwater so can't be there for repairs and service issues that come up. I rely heavily on my local partners to be my eyes, ears and cover my back. Bay Area's service technician was there when he said he was and found the problem required a simple maintenance fix and gave me an overall diagnostic of my system. Keep doing what you're doing guys ~
Annual service contract maintenance tune up and cleaning on a 3.5 ton Carrier heat pump system.
AC SERVICE REPAIR ON A 4 TON CARRIER HEAT PUMP SYSTEM. REMOVED REFRIGERANT,SYSTEM OVERCHARGED.
Annual ac maintenance tune up and cleaning on a 2.5 ton Carrier Performance heat pump system.
AC SERVICE REPAIR ON A 2 TON CARRIER HEAT PUMP SYSTEM. REPLACED FLOAT SWITCH.
AC SERVICE REPAIR ON A 3 TON CARRIER INFINITY GREENSPEED HEAT PUMP SYSTEM. Cleaned pan and drainline.
AC SERVICE REPAIR ON A 3.5 TON CARRIER INFINITY HEAT PUMP SYSTEM. ORDERED BLOWER MOTOR AND MODULE.
Annual ac maintenance tune up and cleaning on a 5 ton Carrier Infinity heat pump system.
AC SERVICE REPAIR ON A 3 TON CARRIER HEAT PUMP SYSTEM. REPLACED STAT WIRE TO CONDENSER.
AC SERVICE REPAIR ON A 5 TON CARRIER INFINITY HEAT PUMP SYSTEM. REPLACED FILTER.
Cleaned out clogged drain line Ruud system