for Brooksville, FL
Kevin - Brooksville, FL
The service technician did a great job diagnosing the problem and doing the necessary repairs. Pete did a great job and thorough work. Thank you.
Sager - Brooksville, FL
Great service as usual. Rep was on time and did a great job.
Lynne - Brooksville, FL
Right on time!
Wendy - Brooksville, FL
Always get great service from Bay Area!
Excellent service as always
Bob - Brooksville, FL
Peter the great!!!
Carole Johnsen - Brooksville, FL
McCall - Brooksville, FL
Amanda - Brooksville, FL
Awesome service, explained clearly what the issue was and replaced and handled in a timely manner!! Polite and courteous!!
Finally a tech who cares
Rocco - Brooksville, FL
Douglas - Brooksville, FL
Good job .Called 20 minutes before showing up.I've been a Bay Area customer for over 14 years.
Annual service contract maintenance tuneup and cleaning on a 5 ton TRANE heat PUMP system
Service call completed, mini split unit not cooling properly on arrival, during inspection found unit low of refrigerant, charge system and check for leaks , no leak found at the moment, system refrigerant pressure are on manufactured specs, system is working properly and cooling at this time
ANNUAL SERVICE CONTRACT MAINTENANCE TUNEUP AND CLEANING ON A 4 TON PERFORMANCE STRAIGHT COOL PERFORMANCE SYSTEM
Replaced outdoor fan motor a25 RPM on carrier comfort heat pump air conditioning system in Brooksville
Unplug drain line regular drain line left quote to replace infinity heat pump air conditioning system by carrier in Brooksville
ANNUAL AC MAINTENANCE TUNE UP AND CLEANING ON A 4 TON CARRIER PERFORMANCE HEAT PUMP SYSTEM.
ANNUAL SERVICE CONTRACT MAINTENANCE TUNE UP AND CLEANING ON 4 TON CARRIER PERFORMANCE HEAT PUMP SYSTEM.
Another tune-up on Carrier Comfort package air conditioning system in Brooksville
AC SERVICE REPAIR ON A 2 TON GEMAIRE HEAT PUMP SYSTEM. REPAIRED DEFROST BOARD.
AC SERVICE REPAIR ON A 5 TON TRANE HEAT PUMP SYSTEM. REPLACED CONDENSER COIL